MISCELLANEOUS ELECTRICAL COMPONENTS AND WIRING HARNESS
i. Check electrical terminals for damaged threads and loose mounting (TM 55-1500-323-24). Thread
damage not to exceed 50 percent of one thread.
j. Check terminals, shields, and covers for damage and loose mounting (TM 55-1500-323-24).
k. Check components for damage and loose mounting.
l. Check circuit breakers for condition and loose mounting.
m. Check circuit breaker light indicating panels for cracks, legibility, and loose mounting.
n. Check for damaged or missing nutplates (TM 1-1500-204-23). Replace as necessary.
END OF TASK