PRIMARY AND RESERVE FIRE EXTINGUISHER REMOVAL - continued
(3) Apply corrosion preventive compound to in-
side of vertical outlet ports. Use corrosion
preventive compound (item 63A, App F).
(4) Allow to air dry.
(5) Wipe with a clean cloth. Use cloth (item 52,
a. Check fire extinguisher mounting brackets
and clamps for cracks (para 12.33).
b. Check removed and attaching parts for corro-
sion (para 1.49).
c. Check fire extinguisher tubes for cracks,
dents, nicks, chafing, wear and corrosion
END OF TASK